Flooded starts are probably the major cause of compressor failures. Flooded starts occur when liquid refrigerant has migrated from the system and condensed into the compressor oil. Migration can occur in all systems up to a point, due to the vapour pressure of the refrigerant being greater than the vapour pressure of the oil. It is the refrigerant vapour that migrates and then condenses into the colder compressor oil.
Crankcase heaters can help prevent this problem occurring provided the heater is large enough to raise the oil temperature to at least 10°C above the ambient temperature surrounding the compressor. In cold windy environments the compressor may need an additional belt type crankcase heater plus an insulated jacket to achieve this, and tests should be carried out to confirm that the oil temperature requirements can be satisfied under all ambient temperature conditions.
Long OFF Cycles are also a cause of this problem, especially during the Night, and throughout the Weekends when the plant is least used, and the heat load requirements are minimal. High temperature rooms often suffer this type of failure due to very short duty cycles and lack of heat load during the winter months.
The longer the OFF cycle, the greater the degree of liquid migration. The colder the oil, the greater the degree of liquid to oil migration that takes place.
During the OFF Cycle, when the compressor has stopped, the compressors oil temperature slowly cools down. Under situations where the surrounding ambient temperature is cold or very cold, the refrigerant vapour will start to migrate to the colder part of the system. When this is the compressor, the refrigerant vapour starts to condense inside the compressor and slowly the sump oil becomes diluted with this condensed liquid. As the oil becomes more and more saturated, some of the refrigerant will separate from the oil and lay under the oil/liquid mixture and the less diluted oil will sit above this oil/liquid layer, where it will attract even more liquid. The longer the compressor is idle, the more liquid that migrates.
When the compressor is started, the pressure inside the compressor falls rapidly. At this point the liquid in the sump oil literally explodes out of the oil causing the crankcase to fill with refrigerant foam and oil droplets. Depending on the degree of dilution, the initial problem is that this liquid/oil mix is drawn up into the compressor’s oil ways that feed the bearings and cylinder bores etc.
As this oil/liquid mix is drawn up into the crankshaft to feed the main and big end bearing’s the heat of friction from the bearing surfaces will cause the liquid in the mix to “Flash Off” back into a vapour. This vapour will increase rapidly in its volume and prevent oil reaching the furthest bearings and con rods away from the oil pick up point. These bearings quickly run dry and overheat.
Sometimes on smaller machines the main front or motor end bearing will seize and stall the motor. On larger machines the powerful motor often continues to spin the crankshaft and then the upper most con rods seize onto the crankshaft and as the crankshaft continues to spin, the soft aluminium con rods are snapped and the broken rods then often smash into the pistons causing a total compressor smash up. These metallic particles can be thrown around inside the machine and can damage the motor insulation and cause a spot burn or total motor burn out.
Flooded starts can often be simply diagnosed by high oil levels seen in the oil level sight glass, and during the start-up mode the oil is seen to foam sometimes for only a few seconds, sometimes for a few minutes. The longer the foaming lasts, the more wear and damage is taking place. Engineers can easily diagnose these signs of Flood back problems, but the compressor failures can often be mistaken for Liquid Flood back or Flooded Starts as the failed components often look very similar under inspection.
In extreme migration cases, this oil rich/liquid froth mixture can spill up and over into the suction gallery and into the cylinders through the suction valves. This mixture is partially Non-Compressible and often causes the suction valves to break, which can lead to broken piston crowns and damaged discharge valves and head gaskets. In these extreme cases the cause is deemed as Liquid Slugging.
Typical causes of flooded start:
Crankcase Temperature lower than Evaporator
Long Off Cycle times
Compressor sited in a cold windy environment
Crankcase heater faulty or of insufficient power to achieve required oil temperature
One-time pump down control
Leaky solenoid valve
Preventative measures required:
Use a continuous Pump Down control
Use a belt type crankcase heater plus insulated blanket
Site the compressor in a warmer ambient area
Typical damage to compressor parts:
Washed out bearings
Erratic wear to bearing surfaces
Seized and broken con rods
Main bearing seizures
Total smashed machine
Bearings near to oil pick up point in good condition. Distant bearings washed and scored
Liquid washed bearings always show aluminium con rod particles welded to crankshaft journal